Siemens Intel Active Management Technology of SIMATIC IPCs
1. EXECUTIVE SUMMARY
CVSS v3 6.7
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Siemens
- Equipment: Intel Active Management Technology (AMT) of SIMATIC IPCs
- Vulnerabilities: Cryptographic Issues, Improper Restriction of Operations within the Bounds of a Memory Buffer, Resource Management Errors
2. RISK EVALUATION
Successful exploitation of these vulnerabilities may allow arbitrary code execution, a partial denial-of-service condition, or information disclosure.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following Siemens products are affected:
- SIMATIC FieldPG M5: All versions prior to v22.01.06,
- SIMATIC IPC427E: All versions prior to v21.01.09,
- SIMATIC IPC477E: All versions prior to v21.01.09,
- SIMATIC IPC547E: All versions prior to R1.30.0,
- SIMATIC IPC547G: All versions prior to R1.23.0,
- SIMATIC IPC627D: All versions prior to v19.02.11,
- SIMATIC IPC647D: All versions prior to v19.01.14,
- SIMATIC IPC677D: All versions prior to v19.02.11,
- SIMATIC IPC827D: All versions prior to v19.02.11,
- SIMATIC IPC847D: All versions prior to v19.01.14, and
- SIMATIC ITP1000: All versions prior to v23.01.04
3.2 VULNERABILITY OVERVIEW
A Bleichenbacher-style side channel vulnerability in TLS implementation in Intel Active Management Technology before v12.0.5 may allow an unauthenticated user to obtain the TLS session key via the network.
Multiple buffer overflows in Intel AMT in Intel CSME firmware versions before 12.0.5 may allow a privileged user to execute arbitrary code with Intel AMT execution privilege via local access.
Multiple memory leaks in Intel AMT in Intel CSME firmware versions before 12.0.5 may allow an unauthenticated user with Intel AMT provisioned to cause a partial denial-of-service condition via network access.
- CRITICAL INFRASTRUCTURE SECTORS: Chemical, Critical Manufacturing, Energy, Food and Agriculture, Water and Wastewater Systems
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
Siemens reported these vulnerabilities to NCCIC.
Siemens recommends users upgrade to the latest version. Additional information as well as upgrades can be found at the following link.
The vulnerabilities are resolved in the following versions for each product listed:
- SIMATIC FieldPG M5
- SIMATIC IPC427E
- SIMATIC IPC477E
- SIMATIC IPC547E
- SIMATIC IPC547G
- SIMATIC IPC627D
- SIMATIC IPC677D
- SIMATIC IPC827D
- SIMATIC IPC647D
- SIMATIC IPC847D
- SIMATIC ITP1000
Siemens has identified the following specific workarounds and mitigations users can apply to reduce the risk:
- As a prerequisite for an attack, an attacker must be able to run malicious code on affected systems. Therefore, Siemens recommends determining if it is possible that untrusted code can be run on these systems, or if existing measures implemented by the operator reduce the likelihood of untrusted code being run.
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B–Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
NCCIC also recommends that users take the following measures to protect themselves from social engineering attacks:
- Do not click web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scams for more information on avoiding email scams.
- Refer to Avoiding Social Engineering and Phishing Attacks for more information on social engineering attacks.
No known public exploits specifically target these vulnerabilities.