1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: Paradox
- Equipment: IP150
- Vulnerabilities: Stack-based Buffer Overflow, Classic Buffer Overflow
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow an attacker to remotely execute arbitrary code, which may result in the termination of the physical security system.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Paradox IP150 are affected:
- Paradox IP150 firmware Version 5.02.09
3.2 VULNERABILITY OVERVIEW
The affected product is vulnerable to three stack-based buffer overflows, which may allow an unauthenticated attacker to remotely execute arbitrary code.
The affected product is vulnerable to five post-authentication buffer overflows, which may allow a logged in user to remotely execute arbitrary code.
- CRITICAL INFRASTRUCTURE SECTORS: Multiple Sectors
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: United States
Omri Ben-Bassat of Section 52 at Azure Defender for IoT reported these vulnerabilities to CISA.
Contact Paradox support for mitigation details via email at [email protected]
CISA recommends users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Ensure the least-privilege user principle is followed.
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls and isolate them from the business network.
- When remote access is required, use secure methods, such as virtual private networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices on the ICS webpage on us-cert.cisa.gov. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS webpage on us-cert.cisa.gov in the Technical Information Paper, ICS-TIP-12-146-01B–Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to CISA for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.